- About this Journal ·
- Abstracting and Indexing ·
- Advance Access ·
- Aims and Scope ·
- Annual Issues ·
- Article Processing Charges ·
- Articles in Press ·
- Author Guidelines ·
- Bibliographic Information ·
- Citations to this Journal ·
- Contact Information ·
- Editorial Board ·
- Editorial Workflow ·
- Free eTOC Alerts ·
- Publication Ethics ·
- Reviewers Acknowledgment ·
- Submit a Manuscript ·
- Subscription Information ·
- Table of Contents

International Journal of Photoenergy

Volume 2012 (2012), Article ID 381016, 12 pages

http://dx.doi.org/10.1155/2012/381016

## Modified Grid-Connected CSI for Hybrid PV/Wind Power Generation System

^{1}Department of Electrical Engineering, Chiangmai University, Suthep, Muang, Chiangmai 50200, Thailand^{2}Department of Electronics Engineering, University of Electro-Communications, 1-5-1 Chofugaoaka, Chofu, Tokyo 182-8585, Japan^{3}Laboratoire Plasma et Conversion d’Energie (LAPLACE), Institut National Polytechnique de Toulouse, 31071 Toulouse, France

Received 8 April 2012; Revised 15 August 2012; Accepted 24 August 2012

Academic Editor: Christophe Menezo

Copyright © 2012 D. Amorndechaphon et al. This is an open access article distributed under the Creative Commons Attribution License, which permits unrestricted use, distribution, and reproduction in any medium, provided the original work is properly cited.

#### Abstract

The principle of a power conditioning unit for hybrid PV/wind power generation system is proposed. The proposed power conditioner is based on the current source inverter (CSI) topology. All energy sources are connected in parallel with a DC-bus through the modified wave-shaping circuits. To achieve the unity power factor at the utility grid, the DC-link current can be controlled via the wave-shaping circuits with the sinusoidal PWM scheme. In this work, the carrier-based PWM scheme is also proposed to minimize the utility current THD. The power rating of the proposed system can be increased by connecting more PV/wind modules through their wave-shaping circuits in parallel with the other modules. The details of the operating principles, the system configurations, and the design considerations are described. The effectiveness of the proposed CSI is demonstrated by simulation results.

#### 1. Introduction

The steadily increasing energy consumption for the conventional energy sources like a fossil-energy-based fuel has created much interest in the alternative energy sources. Many renewable energy sources are now developed and being widely used. These energy sources can be integrated to form a hybrid system which is an excellent option for distributed energy product. In general, the hybrid systems have better potential to provide higher quality and more reliable power than the single source systems. Recently, the solar and wind energy are the most commonly used renewable energy sources in a hybrid system due to the high efficiency and reliability to supply the continuous power to the load or the utility grid. The typical hybrid power generation system is shown in Figure 1(a). This system includes the energy sources, DC-DC converters, a DC-AC inverter, and the utility grid. All energy sources are connected in parallel to a common DC-AC inverter through their individual DC-DC converters.

Several configurations of hybrid PV/wind power generation systems, applying the various static converter topologies, have been proposed in the literatures [1, 2]. Previous approaches of the hybrid PV/wind power converters were mainly based on voltage source inverter (VSI) topology. One of the commonly used VSI for hybrid PV/wind is shown in Figure 1(b). In this topology, all energy sources are connected to a common DC-bus through the individual DC-DC boost converters. The DC-DC converters are responsible for tracking the maximum power of the wind and PV sources under all operating conditions. The outputs of both DC-DC converters are then connected to a single-phase DC-AC inverter. The DC-link voltage will be regulated by the DC-AC inverter with the current-regulated PWM control to achieve the unity power factor at the utility grid. Nowadays VSI has received a lot of attention but the high switching losses of the switching devices in both conversion stages are still a major drawback of this topology. To overcome this problem, several power converters based on the current source inverter (CSI) topology have been developed [3–8]. Compared with the VSI topology, CSI topology has the ability to boost the output voltage without an additional boost converter [4, 9]. Therefore, CSI is strongly suggested for the grid-connected systems which the magnitude of the DC input voltage is lower than the peak of utility voltage. In addition, CSI generally features simple converter structure and reliable short-circuit protection. Furthermore, the application of CSI for hybrid PV/wind grid-connected system has not been reported in the previous publications.

In this paper, a modified grid-connected CSI for hybrid renewable energy systems consisting of PV and wind is proposed. The details of the operation principle and the system configuration are also discussed. The simulation setup has been carried out to verify the system performance of the proposed ideas under the different scenarios.

#### 2. Operating Principles

##### 2.1. Overview Concept of the Proposed System with DC-Link Current Sharing Technique

In this section, the overview of the proposed hybrid PV/wind power generation system as shown in Figure 2 can be introduced. The proposed system consists of two constant current sources and , two current wave-shaping circuits (can be named as DC-DC chopper), an unfolding circuit, and a low-pass filter. Two constant current sources are connected in parallel to a common DC-bus through their own current wave-shaping circuits. Both wave shaping circuits, operating in the same switching frequency, are used to perform the PWM output currents and at a DC-bus. In order to supply active power to the utility grid, the DC-link current is controlled to be in phase with the utility voltage . Therefore, the unity power factor can be achieved. The unfolding circuit is used to produce a unipolar pulse-width modulation (PWM) current by setting the direction of a PWM current at a DC link. At the last stage, low-pass filter is connected to eliminate the high-frequency harmonic components in a unipolar PWM current before injected to the utility grid.

In Figure 2(b), the waveforms of , , , and in the block diagram in Figure 2(a) are shown. According to Kirchhoff’s current law (KCL), it can be seen that the PWM current at a DC-bus is the sum of output currents from the two wave-shaping circuits and , respectively. Hence, the instantaneous DC-link current can be determined by . In addition, the magnitude of can be found by summing the magnitude of and (), respectively. As a result, the magnitude of can be independently controlled by two constant current sources and , respectively.

##### 2.2. Circuit Configuration and Control Strategy

Figure 3(a) shows the circuit topology of the proposed grid-connected CSI for hybrid PV/wind power generation. The circuit diagram differs from that of a VSI in Figure 1(b) by the absence of a DC-link capacitor . The proposed circuit is composed of two wave-shaping circuits, a thyristor-based H-bridge inverter, and low-pass filter. Input renewable energy sources, PV and wind, are connected to a common DC-bus through their own wave-shaping circuits. The proposed system control scheme is also illustrated in Figure 3(b).

On the DC-side of the inverter, the DC chokes and are required to provide the smooth and continuous DC currents and , respectively. Chopper switches and can be controlled to shape the constant input DC current and to be the PWM currents and , respectively, at a DC-bus. To achieve the unity power factor at the utility grid, the utility current is required to be sinusoidal and in phase with the utility voltage . Thus the voltage will be rectified to establish a full-wave rectified sinusoidal signal , where is an absolute gain. In the same time, the maximum power point tracker (MPPT) can be used for tracking the maximum power of PV and wind by multiplying the reference signal with the MPPT reference of each energy source and to produce the modulating signal and , respectively. In PV array, an MPPT algorithm is used to determine the optimal operating point . The optimal current is calculated and tracked from measured valued of PV voltage and PV current . Similarly, for the wind turbine, the extracted power of the wind turbine and wind speed are measured. The optimal point can be provided by the MPPT controller. In both energy sources, and are the constant gain of the MPPT controller of PV and wind, respectively.

To obtain the control signal of chopper switches and , the modulating signals and are compared with a triangular-shaped carrier waveform of the switching frequency . The instantaneous DC-link current can be obtained by the summation of and . The H-bridge inverter operates in synchronism with the utility grid and is controlled to provide a unipolar PWM current . The zero-crossing circuit is used to generate the control signal of H-bridge inverter . Switches and are turned on in the positive half-cycle of the grid voltage , whereas and are turned on in the negative half cycle. It can be observed that the inverter current is obtained by unfolding the DC-link current . At the last stage, and form the low-pass filter which attenuates the high frequency components in the inverter output current .

The principle of the PWM scheme for the proposed CSI is illustrated in Figure 4. For the proposed modulation scheme, two modulating waves and are required. Both modulating waves are of the same frequency and synchronize with the utility grid but the magnitudes and are different. The modulating waves and are compared with a common triangular carrier wave , generating two gating signals and for chopper switches and , respectively. It should be noted that the fundamental-frequency component of the inverter current can be expressed as as shown in Figure 4.

##### 2.3. Inverter Mode of Operation

In order to understand the operation details of the proposed grid-connected CSI in Figure 3(a), the equivalent circuit is illustrated in Figure 5. This circuit can be subdivided into two configurations, the input DC-side and the output AC-side, respectively.

For a simplify analysis in each interval of the circuit, the following conditions are assumed.(I)The input voltage sources and and DC chokes and can be considered and modeled as the constant current sources and , respectively.(II)The output voltage at the DC-side can be assumed to be a constant DC voltage source .(III)The input current at the AC-side can be assumed to be a constant DC current source . (IV)All semiconductor switches in the DC-side and the AC-side are operated at the switching frequency () and the grid frequency (), respectively.

###### 2.3.1. DC-Side Operation

For the one switching period, the operation of the converter in the DC-side can be divided into two stages. The equivalent circuit for each stage is shown in Figure 6 and its key waveforms are depicted in Figure 4. Assuming that the modulating signals for energy sources can be defined as . The operation processes of the DC-side are specified as follows.

*Stage 1 (). *When , chopper switches and are on, chopper diodes and are off, the input DC currents and flow through and , respectively. The current and cannot flow through the diodes and , leading to . According to KCL, the DC-link current can be considered as consisting of the sum of diode currents and . That is,

*Stage 2 (). *When , chopper switches and are off, chopper diodes and are on, the input DC currents and flow to the load through and , respectively, resulting in and . Similar to the first stage, the DC-link current is obtained as

The DC-link current for all stages can be rewritten in term of the switching states as follows: where and are the switching states of the chopper switches and , respectively. The switching states and if (in stage 1); otherwise 0 (in stage 2).

###### 2.3.2. AC-Side Operation

In Figure 7, the equivalent circuit in the AC-side is shown. The AC utility voltage can be expressed by , where is the peak of utility voltage. The operation of this side consists of two stages during the switching cycle. The operation can be described as follows.

*Stage 1 (). *When , the inverter switches and are on, and are off, the input DC current flows to the grid through and , respectively. Then the AC utility current equals to .

*Stage 2 (). *The inverter switches and are off, and are on, when . The DC current flows to the grid through and , respectively, resulting in the utility current to be equal to .

Therefore, the utility current can be defined as

It should be noted that the low-pass filter is not considered in this analysis. Hence, the PWM output current is equal to the utility current ().

##### 2.4. PWM Current Analysis

From the PWM scheme in Section 2.2, the analysis of harmonic components in the proposed CSI can be performed. The mathematical expression of the PWM currents and can generally be expressed as follows [3]: where the number of th harmonic component; ; and ; and ; and are the modulation index of PV and wind sources, respectively; and are the peaks of modulating signals for PV and wind sources and , respectively; is the peak of the triangular carrier waveform . Equations (5) are valid to and , respectively.

The DC-link current can be found from Thus,

According to (4) the inverter output current can be obtained by the operating of the unfolding circuit. Hence, the inverter output current can be expressed in terms of its harmonic components as

Under the conditions of and , the waveform of the inverter output current and its harmonic contents in (8) can be shown in Figure 8. It can be observed that the waveform of the inverter current is close to a unipolar PWM waveform. We can consider at the conditions of and , the current simplified as follows: From this result, the PWM inverter current can be shown in Figure 9(a). This waveform is similar to a unipolar PWM waveform. Figure 9(b) shows the harmonic spectrum of the inverter current . It can be seen that the current has harmonics at the multiples of the switching frequency, that is, at , , and so on. The harmonics of significant magnitudes also appear in the side bands of the switching frequency and its multiples.

##### 2.5. Carrier-Based PWM Scheme

In order to reduce the harmonic distortion in the inverter output current , a carrier-based PWM scheme can be proposed. In general, this scheme can be classified into two categories: phase-shifted and level-shifted modulations. In this paper, a phase-shifted modulation is only studied and applied to the proposed hybrid PV/wind power systems. Normally, the hybrid PV/wind system may be connected in parallel more than two energy sources. The energy sources require triangular carrier signals. For the phase-shifted multicarrier modulation, the carrier waves for each module and are of same amplitude and frequency, but there is a phase shift between any the adjacent carrier waves, given by

For the proposed hybrid PV/wind system as shown in the Figure 3(a), there are two energy sources for system. The modulating signals and have the same frequency but the amplitude is different depending on the MPPT signals of each module. According to (10), the phase shift between each carrier wave and is 180°. The gate signals and are generated by comparing the modulating wave and with the carrier waves and , respectively. The principle of the proposed phase-shifted modulation for the hybrid PV/wind system can be shown in Figure 10. The inverter operates under the conditions of and . The inverter PWM current can be expressed in terms of Fourier series as [3] The inverter output current waveform based on phase-shifted multicarrier modulation is shown in Figure 11(a), and its spectrum is also illustrated in Figure 11(b). The operating conditions are , Hz, and kHz. The inverter current has harmonics and sidebands at the multiple of the twice switching frequency, that is, , , and so on. It is clear that the current waveform is formed by five current steps: , , 0, , and , resulting in a further reduction in THD.

#### 3. Design Consideration

##### 3.1. Input DC Choke Design

Large inductors and are used in the DC-side of the inverter, which make the input voltage sources and appear as the constant DC current sources and . When the chopper switch is turned on, the inductor current rises and the energy is stored in the inductor. If switch is turned off, the energy stored in the inductor is transferred to the AC-side through the diode and the inductor current falls. To design the value of this inductor, the inductor stored energy must be considered. When the switch is turned on, the energy stored in the inductor is where choke inductance, average input power at DC-side, switching period, turn-on time, and average input current. The choke inductance can be expressed as where converter efficiency, average output power at AC-side, and switching frequency.

##### 3.2. Output Low-Pass Filter Design

In order to reduce the high-frequency harmonics in the PWM output current of the grid-connected inverter, a low-pass filter is needed. Passive low-pass filters are normally used as , , , and filters. In this paper, a simple low-pass filter is chosen. A detailed analysis is not considered in this paper. Following the design procedure of [10], the inductor and capacitor can be found through the following equations: where is the amplitude of the grid voltage .

#### 4. Results and Discussion

To verify the proposed grid-connected CSI for hybrid PV/wind system with a simple current-sharing technique, the simulation setup has been designed and carried out with PSIM. It should be noted that the MPPT operating for PV and wind energy is not studied in this paper. The circuit parameters are shown in Table 1. The PV and wind energy sources and and input DC chokes and are modeled by DC current sources and , respectively.

Figure 12 confirms the principle of PWM strategy for the proposed CSI operating under the condition of and . The gate signals for all switches in CSI , , , , , and are also shown in Figure 12. Figures 13, 14 and 15 show the simulated waveform for the proposed CSI, operating under the different conditions, (a) and ; (b) and ; (c) and . The following can be observed.(a)The two different currents and can be combined to produce the current at a DC-bus.(b)The amplitude of can be determined by . The magnitude of and can be independently controlled by the output power of each energy source.(c)The unfolding circuit has two complementary switch pairs (, and , ) switching at line frequency 50 Hz. The unipolar PWM current is performed by unfolding the DC-link current .(d)The waveform of the grid current is close to sinusoidal with low THD. The low amount of harmonic distortion is due to the elimination of high-order harmonic contents by the filtering effect of low-pass filter.

Figure 16 shows the simulated waveforms for the proposed CSI, operating at higher switching frequency. It can be observed that the proposed converter can produce a smooth AC current at the utility grid with low harmonic components. The waveforms of the proposed grid-connected CSI for hybrid PV/wind system with phase-shifted multicarrier modulation are shown in Figure 17. It can be noted that the inverter output current waveform is formed with five current levels.

In higher power applications, the increasing of output power rating of a hybrid PV/wind power generation system is required. It can be achieved by connecting more PV/wind modules in parallel with the other modules through their own DC-DC chopper to a common DC-bus. The configuration of multimodules PV/wind system with all modules connected in parallel is shown in Figure 18. The waveforms of the converter can be shown in Figure 19.

#### 5. Conclusion

A grid-connected inverter for hybrid PV/wind power generation system was proposed. The proposed inverter was based on the current source inverter (CSI) topology. A number of issues were investigated, including the simple current sharing technique, the inverter configuration, operating principle, PWM strategy technique, PWM current analysis, and design consideration. The emphasis of this paper was on the new power converter scheme, where the operating analysis was discussed in details. The proficiency of the proposed inverter was accessed through the computer simulation under the different operation conditions. The performance of the proposed CSI was confirmed by the simulation results.

#### Acknowledgments

This work is supported in part by Thailand Research Fund (TRF) through the Royal Golden Jubilee Ph.D. program under Grant no. PHD/0166/2550, by the French Government’s contribution to the RGJ-Ph.D program, and by the Energy Policy and Planning Office (EPPO), Ministry of Energy, Thailand. This work is also supported by National Research University (NRU) Project from Office of the Higher Education Commission of Thailand.

#### References

- Y. M. Chen, Y. C. Liu, S. C. Hung, and C. S. Cheng, “Multi-input inverter for grid-connected hybrid PV/wind power system,”
*IEEE Transactions on Power Electronics*, vol. 22, no. 3, pp. 1070–1077, 2007. View at Publisher · View at Google Scholar · View at Scopus - C. Liu, K. T. Chau, and X. Zhang, “An efficient wind-photovoltaic hybrid generation system using doubly excited permanent-magnet brushless machine,”
*IEEE Transactions on Industrial Electronics*, vol. 57, no. 3, pp. 831–839, 2010. View at Publisher · View at Google Scholar · View at Scopus - P. G. Barbosa, H. A. C. Braga, M. C. B. Rodrigues, and E. C. Teixeira, “Boost current multilevel inverter and Its application on single-phase grid-connected photovoltaic systems,”
*IEEE Transactions on Power Electronics*, vol. 21, no. 4, pp. 1116–1124, 2006. View at Publisher · View at Google Scholar · View at Scopus - Y. Chen and K. Smedley, “Three-phase boost-type grid-connected inverter,”
*IEEE Transactions on Power Electronics*, vol. 23, no. 5, pp. 2301–2309, 2008. View at Publisher · View at Google Scholar · View at Scopus - N. Vázquez, H. López, C. Hernández, E. Vázquez, R. Osorio, and J. Arau, “A different multilevel current-source inverter,”
*IEEE Transactions on Industrial Electronics*, vol. 57, no. 8, pp. 2623–2632, 2010. View at Publisher · View at Google Scholar · View at Scopus - R. T. H. Li, H. S. H. Chung, W. H. Lau, and B. Zhou, “Use of hybrid PWM and passive resonant snubber for a grid-connected CSI,”
*IEEE Transactions on Power Electronics*, vol. 25, no. 2, pp. 298–309, 2010. View at Publisher · View at Google Scholar · View at Scopus - B. M. T. Ho and H. S. H. Chung, “An integrated inverter with maximum power tracking for grid-connected PV systems,”
*IEEE Transactions on Power Electronics*, vol. 20, no. 4, pp. 953–962, 2005. View at Publisher · View at Google Scholar · View at Scopus - G. Ertasgin, D. M. Whaley, N. Ertugrul, and W. L. Soong, “Implementation and performance evaluation of a low-cost current-source grid-connected inverter for PV applications,” in
*Proceedings of the IEEE International Conference on Sustainable Energy Technologies (ICSET '08)*, pp. 939–944, November 2008. View at Publisher · View at Google Scholar · View at Scopus - M. Kazerani, Z. C. Zhang, and B. T. Ooi, “Linearly controllable boost voltages from tri-level PWM current-source inverter,”
*IEEE Transactions on Industrial Electronics*, vol. 42, no. 1, pp. 72–77, 1995. View at Publisher · View at Google Scholar · View at Scopus - B. Bouneb, D. M. Grant, A. Cruden, and J. R. McDonald, “Grid connected inverter suitable for economic residential fuel cell operation,” in
*Proceedings of the European Conference on Power Electronics and Applications*, p. 10, September 2005. View at Scopus