Research Article  Open Access
Huiwen He, Lei Wang, Peihong Zhou, Fei Yan, "Overvoltage and Insulation Coordination of Overhead Lines in MultipleTerminal MMCHVDC Link for Wind Power Delivery", International Journal of Rotating Machinery, vol. 2017, Article ID 4849262, 7 pages, 2017. https://doi.org/10.1155/2017/4849262
Overvoltage and Insulation Coordination of Overhead Lines in MultipleTerminal MMCHVDC Link for Wind Power Delivery
Abstract
The voltagesourced converterbased HVDC link, including the modular multilevel converter (MMC) configuration, is suitable for wind power, photovoltaic energy, and other kinds of new energy delivery and gridconnection. Current studies are focused on the MMC principles and controls and few studies have been done on the overvoltage of transmission line for the MMCHVDC link. The main reason is that environmental factors have little effect on DC cables and the singlephase/pole fault rate is low. But if the cables were replaced by the overhead lines, although the construction cost of the project would be greatly reduced, the singlepole ground fault rate would be much higher. This paper analyzed the main overvoltage types in multipleterminal MMCHVDC network which transmit electric power by overhead lines. Based on ±500 kV multipleterminal MMCHVDC for wind power delivery project, the transient simulation model was built and the overvoltage types mentioned above were studied. The results showed that the most serious overvoltage was on the healthy adjacent line of the faulty line caused by the fault clearing of DC breaker. Then the insulation coordination for overhead lines was conducted according to the overvoltage level. The recommended clearance values were given.
1. Introduction
The voltagesourced converter (VSC) based highvoltage DC (HVDC) transmission system is considered for a wide range of applications for wind power, photovoltaic energy, or other kinds of new energy delivery and gridconnection due to flexibly control of active power and reactive power output capability [1–4]. The Nanhui MMCHVDC demonstration project and the Nanao multipleterminal MMCHVDC link have been put into operation already and achieved the stable and reliable wind power transmission [5, 6].
At present, the study focuses on the MMC principles and controls and less research has been done on the overvoltage of transmission line for the MMCHVDC project. And there are few studies on the overvoltage characteristics of multiterminal MMCHVDC [7, 8]. State Grid Beijing Economic and Technical Research Institute has done research on the Dalian MMCHVDC project considering the short circuit fault at AC bus, grid side and valve side of connection transformer, smoothing reactor, and DC pole bus. According to the simulation results of overvoltage, the reference voltage and switching impulse withstanding voltage of MOAs in the converter station were determined [9]. Based on the Trans Bay MMCHVDC project, Zhejiang University studied the 14 kinds of fault and found the most serious overvoltages were caused by the singlephase grounding fault at valve side of converter transformer, the short circuit of transformer, the ground short circuit fault at valve head, DC bus grounding fault, and DC line grounding fault. The MOA configuration and insulation coordination scheme were proposed. The withstanding voltages of equipment were determined by deterministic method and the margin coefficient between withstand voltage and impulse overvoltage could be selected as 15%, 20%, and 25% for switching impulse, lighting impulse, and steep impulse, respectively [10].
The researches mentioned above were focused on the converter station. Most of the MMCHVDC projects adopt cables for power transmission all around the world. The cables buried in the ground are not affected by the surrounding environment, so the failure rate is lower [11, 12]. However, cables lines are expensive and the overhead lines can greatly reduce the cost of construction. The overhead lines are susceptible to the surrounding environment, such as lightning and pollution, and the singlepole grounding fault rate is much higher than using cable lines. Therefore, it is necessary to study the overvoltage generated by overhead line faults to support the design of line insulation.
This paper focuses on the overvoltage level of overhead lines in multipleterminal MMCHVDC project. Firstly it pointed out the main overvoltage types of overhead lines in multipleterminal MMCHVDC link. Based on an ±500 kV multipleterminal MMCHVDC for wind power delivery project, the transient simulation model was built and various overvoltage types mentioned above were studied. Then the insulation coordination for overhead lines was conducted according to the overvoltage level. In the end the recommended clearance values were given.
This paper is organized as follows. Section 2 is devoted to analyzing the main overvoltage types of overhead lines in multipleterminal MMCHVDC link and the differences between it and conventional pointtopoint LCCHVDC project while Section 3 presents the simulation overvoltage results based on a multipleterminal MMCHVDC project according to Section 2. Then insulation coordination for overhead lines is conducted and the recommended clearances are given in Section 4. Finally, conclusions are drawn in Section 5.
2. Overvoltage Types of Overhead Line in MultipleTerminal MMCHVDC Project
LCCHVDC systems are usually 2 terminals adopting overhead transmission lines and the occurrence probability of singlepole grounding fault is the highest. Statistical data show that the singlepole lightning flashover rate of ±500 kV DC transmission lines is 0.28 times per 100 km every year. In a bipolar operation, a grounding fault occurring at one pole will induce the slow front overvoltage at the sound pole through the coupling between two poles and reflection and refraction of traveling wave at both ends of line. The magnitude of the overvoltage can be estimated by the following formula:where and are zero sequence and positive sequence wave impedance of transmission line, respectively; is the grounding resistance.
The induced overvoltage at sound pole caused by singlepole grounding fault should also be considered for overhead lines in multipleterminal MMCHVDC project and the magnitude of the overvoltage can be estimated by formula (1) too. In order to improve the availability of MMCHVDC project, the DC circuit breaker would be installed for fault clearing at DC side. So the line fault clearing overvoltage and reclosing overvoltage should be considered.(1)The line fault clearing overvoltage mainly refers to the overvoltage on the sound pole line and the adjacent sound line generated by the fault tripping. It is equivalent to superimposing a current source with a reverse fault current on the circuit breaker when the circuit breaker interrupts the fault current. The current wave propagation and reflection on the adjacent sound line form transient overvoltage. The fault current is related to the main circuit parameters of converter station, the operation characteristics of DC circuit breaker, and the fault grounding resistance.(2)When the DC line is switched on or reclosing, the overvoltage is generated due to the difference between the initial voltage of the line to the ground and the forced voltage at the end of the transition process. The magnitude of the overvoltage can be estimated by the following formula:where is the forced voltage at the end of the transition process and is the initial voltage of the line to the ground.
Therefore 3 kinds of overvoltage are as follows, which should be studied for overhead lines of multiterminal MMCHVDC systems:(1)Induced overvoltage on healthy pole line caused by singlepole grounding fault(2)Fault clearing overvoltage(3)Closing and reclosing overvoltage.
3. Analysis of Overvoltage of Overhead Transmission Lines in MultipleTerminal MMCHVDC Project
3.1. Simulation Parameters
3.1.1. Main Circuit Parameter
A 4terminal ±500 kV MMCHVDC for wind power delivery project, using half bridge and real bipolar connection, has 245 levels and DC rated voltage is 535 kV. The rated voltage of AC power network is 230 kV at delivery end A, which can send wind power out with 17 kA threephase short circuit current, and the rated capacity of A is 3000 MW under the normal operation in island. The rated voltage of AC power network is 230 kV at delivery end B, which can send wind power out with 17 kA threephase short circuit current, and the rated capacity of B is 1500 MW under the normal operation in island. The rated voltage of AC power network is 525 kV at delivery end C, which can send wind power out with 18 kA threephase short circuit current, and the rated capacity of C is 1500 MW. The rated voltage of AC power network is 525 kV at delivery end D, which can send wind power out with 63 kA threephase short circuit current, and the rated capacity of D is 3000 MW.
The lengths of DC transmission lines of 4terminal system are shown in Figure 1. The type of conductors is 4 × JL/G2A720/50 with 12.8 m pole distance, and the type of ground wire is OPGW150 with 12 m horizontal distance, together with the model JNRLH60/G1A400/35 of metallic return line which has the horizontal distance of 9 m. Typical tower model of tangent tower is shown in Figure 2, and the transmission line is simulated by Frequency Dependent (Phase) Model in PSCAD. In the converter station, the current limiting reactors are arranged on the pole lines and the metallic return lines; the values of reactance are 150 mH on the pole line and 300 mH on the neutral line. The reference voltage of pole line arrester is 629 kV and residual voltage is 904 kV under switch operation with 2 kA current.
According to empirical equation (3), the arc resistance in the air can be calculated:where is the length of arc and is the rms. of current with the unit ampere. In the simulation, the sum resistance of arc and grounding tower is 4 .
3.1.2. Control and Protection Model of Converter Station
A double closedloop controller is established in PSCAD to achieve converter stationlevel control. Double closedloop control can be divided into an outer loop controller and an inner loop controller. The outer loop controller can calculate the current reference value of the currentmode inner loop controller according to the active and the reactive power command. The inner loop controller keeps the dq axis current tracking its reference value by adjusting the output voltage of the inverter. The control system used in the simulation is shown in Figure 3 [13–16].
According to Figure 3, the dynamic differential equation of AC side in threephase stationary coordinate system is shown as where , and are the measured phase A, phase B, and phase C voltages at grid side of converter transformer, respectively. , , and are the measured phase A, phase B, and phase C currents at grid side of converter transformer, respectively. , , and are the measured phase A, phase B, and phase C voltages at valve side of converter transformer, respectively. is the equivalent reactance. is the equivalent resistance.
After the park transformation, the active power injected into the converter station from the AC system is as (5). The reactive power injected into the converter station from the AC system is as (6). So the decoupled control of active power and reactive power can be realized:where and are the axis and axis voltages derived from park transformation of , , and , respectively. and are the axis and axis currents derived from park transformation of , , and , respectively.
3.1.3. Wind Power Model
Two wind farms provide the power sources for 2 substations of the 4terminal ±500 kV MMCHVDC project. In order to calculate the accurate overvoltage level, the influence of the wind farms on overvoltage was considered.
In the simulation, the electromagnetic transient model based on the transform of doubly fed induction generator was established. The coordinate system based on rotation speed of rotor was adopted. The voltage and current on the armature side and the exciting side satisfy [17]where and are voltages on the armature side and the exciting side, respectively. and are resistance on the armature side and resistance on the exciting side, respectively. and are currents on the armature side and the exciting side, respectively. and are flux linkage matrixes on the armature side and the exciting side, respectively. ω is the angular velocity of rotor rotation.
3.2. Overvoltage Analysis
Two modes of operation are considered during the simulation:(1)Normal mode:
All the stations access the network.(2)Abnormal mode:
Some of the stations are unconnected to the network, which leads to a longer transmission line than normal mode.
The specific calculation process is as follows. The DC operation voltage is 535 kV before fault. The fault line is divided into 10 sections. Along the line each section is grounded. Then the circuit breakers at the ends of fault line trip remove the temporary ground fault, and after the delay time the DC circuit breakers reclose. Both the overvoltages caused during the grounding and reclose processes are taken into consideration. Besides, the overvoltages caused by faults on other lines should be calculated too.
3.2.1. Normal Mode
The overvoltage levels of all pole lines are shown in Table 1. The maximum overvoltage of 990.77 kV (1.85 p.u., 1 p.u. = 535 kV) appeared in the BC line, caused by the AD line fault. The overvoltage distribution and probability distribution of BC line are shown in Figure 4. The statistics overvoltage along the line is umbrella type distribution. In the middle of line the overvoltage is high and to both ends of the line diminishing. This is due to the installation of the arrester on the pole line bus, which can suppress the overvoltage.

3.2.2. Abnormal Mode
The overvoltage levels of all pole lines were simulated under abnormal mode, which means some of the stations were unconnected to the DC grid during the simulations. The maximum overvoltage, out of hundreds of simulation results of different unconnected stations, occurred in case C station is unconnected. In this section, overvoltages of transmission lines when C station is unconnected are shown in Table 2. The maximum overvoltage has the peak of 1034 kV (1.93 pu), appearing in the CD line, caused by the AB positive line ground fault. The overvoltage distribution and probability distribution of CD line are shown in Figure 5, under situation of the unconnected C station. The maximum overvoltage waveform and the corresponding pole bus waveform are shown in Figure 6. It can be seen that the maximum overvoltage occurs during the DC circuit breaker opening process. Depending on the time difference between peaks, the peaks of the waveform in Figure 6 were caused by the different wave velocities of reflected positive sequence and zero sequence waves.

4. Insulation Coordination of Pole Lines
According to IEC 600713, the switching impulse 50% flashover voltage of air gap between wire and tower can be calculated in (10), which can be used for insulation coordination of pole lines:
where is maximum voltage of system (535 kV in this paper), is discharge voltage correction coefficient of air density and humidity of the switch impulse voltage, is the per unit value of overvoltage, and is the standard deviation.
Altitude correction can be conducted by IEC 600712 with safety margin. The calculation formula is showed by where is the altitude above sea level measured in meters and the value of depended on the type of voltage impulse.
The discharge curve of air gap of double circuit tower is provided by CEPRI tested on upper layer of ±500 kV DC double circuit transmission line, and the discharge curve of air gap of single circuit tower is tested on ±500 kV real type tower with Vtype insulator string. The air gap flashover curve could be obtained by referring to relevant papers [18]. The calculated air gaps of single circuit and double circuit on one tower under switch impulse voltage are shown in Table 3. The required values of air gaps are considered under normal mode and abnormal mode (without C substation).

5. Conclusion
(1)It is different from circuit breaker adopted MMCHVDC system and LCCHVDC when confronted with overvoltage of transmission line. In LCCHVDC, only the induced overvoltage on sound line caused by singlepole line fault is considered. Besides the induced overvoltage, the fault clearing overvoltage and reclosing overvoltage of transmission line have to be taken into consideration in the case of multiterminal MMCHVDC project.(2)The statistics overvoltage on the sound line caused by ground fault presents the umbrella type distribution along the line. In the middle of line the overvoltage is high and to both ends of the line diminishing. In this paper, the simulated overvoltage of the project is up to 1.93 p.u., occurring during the DC circuit breaker clearing the DC side failure. The suppression measures of DC circuit breaker causing overvoltage need further study.(3)The required minimal clearance of pole lines under switch impulse overvoltage can be selected as 2.79 m at an altitude of 0 m. Differential air gap selection for various transmission lines is also recommended.(4)The mechanism for the generation of overvoltages has not been clearly explained. The quantitative influence of the line length, the grounding mode of the valve side of converter, and the network structure on the overvoltage level should be further studied to support the project design.
Conflicts of Interest
The authors declare that there are no conflicts of interest regarding the publication of this paper.
Acknowledgments
The authors are grateful for the support provided by the National Key Research and Development Program of China (Grant 2016YFB0900900) and the SGCC Project of Overvoltage and Insulation Coordination Technology Research of ±500 kV Flexible DC Grid (GY7115076).
References
 H. Zhiyuan, Y. Zhao, and T. Guangfu, “Key Technology Research and Application of the ±320 kV/1000 MW VSCHVDC,” Smart Grid, vol. 4, pp. 124–132, 2016. View at: Google Scholar
 M. Weimin, W. Fangjie, Y. Yiming et al., “Flexible HVDC Transmission Technology’s Today and Tomorrow,” High Voltage Engineering, vol. 40, pp. 2429–2439, 2014. View at: Google Scholar
 T. Guangfu, H. Zhiyuan, and P. Hui, “Discussion on Applying the VSCHVDC Technology in Global Energy Interconnection,” Smart Grid, vol. 4, no. 2, pp. 116–123, 2016. View at: Google Scholar
 H. Alyami and Y. Mohamed, “Review and development of MMC employed in VSCHVDC systems,” in Proceedings of the 2017 IEEE 30th Canadian Conference on Electrical and Computer Engineering (CCECE), pp. 1–6, April 2017. View at: Publisher Site  Google Scholar
 L. Xingyuan, Z. Qi, W. Yuhong et al., “Control strategies of voltage source converter based direct current transmission system,” Gaodianya Jishu/High Voltage Engineering, vol. 42, no. 10, pp. 3025–3037, 2016. View at: Publisher Site  Google Scholar
 N. Zhang, C. Kang, D. S. Kirschen et al., “Planning pumped storage capacity for wind power integration,” IEEE Transactions on Sustainable Energy, vol. 4, no. 2, pp. 393–401, 2013. View at: Publisher Site  Google Scholar
 J. Lyu, X. Cai, and M. Molinas, “Frequency Domain Stability Analysis of MMCBased HVdc for Wind Farm Integration,” IEEE Journal of Emerging and Selected Topics in Power Electronics, vol. 4, no. 1, pp. 141–151, 2016. View at: Publisher Site  Google Scholar
 H. Chang, D. Chen, Y. Wu, and Y. Ma, “Analysis and optimization strategy of power disturbance on Xiamen flexible HVDC project,” Gaodianya Jishu/High Voltage Engineering, vol. 42, no. 10, pp. 3045–3050, 2016. View at: Publisher Site  Google Scholar
 M. Weimin, J. Weiyong, and L. Yanan, “System design for dalian VSCHVDC power transmission project,” Electric Power Construction, vol. 34, no. 5, pp. 1–5, 2013. View at: Google Scholar
 Z. Xu, G. Liu, and Z. Zhang, “Research on fault protection principle of DC grids,” Gaodianya Jishu/High Voltage Engineering, vol. 43, no. 1, pp. 1–8, 2017. View at: Publisher Site  Google Scholar
 F. B. Ajaei and R. Iravani, “Cable surge arrester operation due to transient overvoltages under DCside faults in the MMCHVDC link,” IEEE Transactions on Power Delivery, vol. 31, no. 3, pp. 1213–1222, 2016. View at: Publisher Site  Google Scholar
 M. Wang, Y. Hu, W. Zhao, Y. Wang, and G. Chen, “Application of modular multilevel converter in medium voltage high power permanent magnet synchronous generator wind energy conversion systems,” IET Renewable Power Generation, vol. 10, no. 6, pp. 824–833, 2016. View at: Publisher Site  Google Scholar
 Z. Chengyong, Modeling and Simulation of Flexible HVDC, China Electric Power Press, Beijing, China, 2014.
 F. Zhang, J. Xu, and C. Zhao, “New control strategy of decoupling the AC/DC voltage offset for modular multilevel converter,” IET Generation, Transmission and Distribution, vol. 10, no. 6, pp. 1382–1392, 2016. View at: Publisher Site  Google Scholar
 Y. Dong, W. Ling, J. Tian et al., “Control protection system for Zhoushan multiterminal VSCHVDC,” Electric Power Automation Equipment, vol. 36, no. 7, pp. 169–175, 2016. View at: Google Scholar
 K. Ou, H. Rao, Z. Cai et al., “MMCHVDC simulation and testing based on realtime digital simulator and physical control system,” IEEE Journal of Emerging and Selected Topics in Power Electronics, vol. 2, no. 4, pp. 1109–1116, 2014. View at: Publisher Site  Google Scholar
 Z. Gu, Y. Tang, W. Liu et al., “Electromechanical transent—electromagnetic transient hybrid simulation of doublefed induction generator,” Power System Technology, vol. 39, no. 3, pp. 615–620, 2015. View at: Google Scholar
 W. Liao, Y. Ding, Z. Sun, and Z. Su, “Altitude correction of switching impulse flashover voltage of tower gaps with Vshaped insulator strings for HVDC power transmission lines,” Dianwang Jishu/Power System Technology, vol. 36, no. 1, pp. 182–188, 2012. View at: Google Scholar
Copyright
Copyright © 2017 Huiwen He et al. This is an open access article distributed under the Creative Commons Attribution License, which permits unrestricted use, distribution, and reproduction in any medium, provided the original work is properly cited.