Research Article  Open Access
Doniazed Sioud, Ahmed Bellagi, "Analysis of Hybrid Ejector Absorption Cooling System", Journal of Engineering, vol. 2019, Article ID 1862917, 13 pages, 2019. https://doi.org/10.1155/2019/1862917
Analysis of Hybrid Ejector Absorption Cooling System
Abstract
In this paper, a hybrid ejector singleeffect lithiumbromide water cycle is theoretically investigated. The system is a conventional singleeffect cycle activated by an external steamejector loop. A mathematical model of the whole system is developed. Simulations are carried out to study the effect of the major parameters of the hybrid cycle on its performances and in comparison with the conventional cycle. The ejector performance is also investigated. Results show that the entrainment ratio rises with steam pressure and condenser temperature, while it decreases with increasing generator temperature. The effect of the evaporator temperature on ejector performance is negligible. It is shown also that the hybrid cycle exhibits better performances than the corresponding basic cycle. However, the performance improvement is limited to a specific range of the operating parameters. Outside this range, the hybrid system behaves similar to a conventional cycle. Inside this range, the increases, reaches a maximum, and then decreases and rejoins the behavior of the basic cycle. The maximum , which can be as large as that of a conventional doubleeffect cycle, about 1, is obtained at lower temperatures than in the case of singleeffect cycles.
1. Introduction
Cooling and air conditioning are essential for small scale and large industrial process applications. While systems applying the vaporcompression technique use environmental harmful refrigerants (FCC, FCHC, etc.), absorption technique for production of cold is based on environment friendly working fluids, namely, aqueous lithium bromide solutions with water as refrigerant or waterammonia mixtures with ammonia as refrigerant. This technique however suffers from low performances. That is the reason why new hybrid and combined configurations are proposed, implying the integration of new components, particularly ejectors, in order to enhance the performances.
Various configurations incorporating ejectors were studied. Exhaustive review of the literature on this subject can be found in Besagni et al. [1, 2]. Elaborated CFDmodels of ejectors developed to evaluate the ejector performances in both ondesign and offdesign conditions have been also published [3]. Combined cycles were investigated with ejector set at the absorber inlet [4–9]. of such cycles are reported to be higher by about 2–4% than that of conventional cycles. Principally, investigations indicate that of the combined configuration are greater or equal to that of singleeffect cycles, but reached at lower generator temperatures.
Other configurations are discussed where the ejector is located at the condenser inlet of singleeffect systems [10–14]. Theoretical investigations confirm the improvement of the performances in comparison with basic singleeffect cycles. Experimental studies [15] show that this combined cycle is 3060% more performant than conventional absorption cycles and almost reaches the of doubleeffect systems. Besides modifying configurations, adding a flash tank between ejector and evaporator was also proposed [16, 17].
Ejector improved doubleeffect absorption system was also investigated [18–20]. The of the proposed refrigeration scheme was found to increase with the temperature of the heat source until this temperature reaches 150°C. Beyond that value, the new cycle worked as a conventional doubleeffect cycle. Another configuration was studied with an ejector coupled to vapor generator [21–23]. This procedure is intended to enhance the concentration process by compressing the vapor produced from the lithium bromide solution in order to reheat the solution from which it came. Results showed that of the new cycle increases especially with the heat source temperature.
In this paper, an ejectoractivated singleeffect LiBrwater cycle is proposed and theoretically investigated. The objective is to assess the feasibility and limits of performance of this new cycle scheme. If the of the proposed system could reach that of a conventional doubleeffect cycle, this would mean obtaining high performance by avoiding the configuration complexity of doubleeffect cycles. We investigate the evolution of the of the hybrid cycle with the steam generator temperature and the main factors of the cooling machine, i.e., desorber, condenser, and evaporator temperature. The behavior of the entrainment ratio as ejector performance criterion is also investigated for various primary and secondary flow pressure and backpressure.
2. System Description
Figures 1(a) and 1(b) are schematics of a conventional singleeffect absorption cycle and an ejectorenhanced singleeffect absorption system. A conventional singleeffect absorption chiller (Figure 1(a)) is composed of evaporator, absorber, condenser, generator, solution expansionvalve, pump, solution heat exchanger, and refrigerant expansionvalve. In a hybrid system (Figure 1(b)) a steamgeneratorejector loop is coupled to the conventional singleeffect installation via the machine generator. This extra circuit is constituted of an ejector, a steam generator, a water pump, and an expansion valve.
(a)
(b)
The ejector loop is intended to improve the cycle performance by enhancing the concentration process in the machine generator. A highpressure flow coming from the external steam generator enters the primary nozzle of the ejector where its pressure drops while it is accelerated. At the nozzle exit section (Figure 2) its velocity becomes supersonic and high enough to entrain a secondary flow (19 in Figure 1), part of the vapor generated in the desorber. The two streams mix in the mixing chamber and the resulting gas, after undergoing a shockwave that reduces its velocity to subsonic, is compressed in the diffuser forming the last segment of the ejector. The exiting vapor condenses in the coil placed inside the solution generator, liberating thus condensation heat used to concentrate the saline solution by desorbing vapor from the waterrich solution entering the generator. Part of the condensate flows, after appropriate pressure reduction, to the condenser, and the rest is pumped back to the steam generator.
3. Chiller Model
Basing on mass and energy balances written for every machine element a mathematical model of the installation is set up. For the numerical simulations, a computer code of the machine model is realized using the software Engineering Equations Solver, EES [24].
The model is elaborated under the following assumptions:(i)Steady state conditions(ii)Negligible heat losses to the surroundings at generator, condenser, absorber, and evaporator(iii)Negligible pressure losses in pipes and components(iv)Saturated refrigerant exiting condenser and evaporator(v)Isenthalpic flow in solution and refrigerant valves(vi)Phase equilibrium between solution entering refrigerant generator and vapor leaving(vii)Constant solution flowrate leaving the absorber, specifically 2 kg/s(viii)Heat exchanger effectiveness,
In the following major elements of the model are presented.
3.1. Ejector Loop
This loop includes steam generator, ejector, heating coil placed in solution generator, expansion valve, and water pump.(i)Steam Generator
The mass and energy balances on steam generator write, respectively,The properties of exiting saturated vapor are:Further,
Properties with index for water refer to pure water properties as given in steam tables.(ii)Ejector
The ejector performance depends on the backpressure —the pressure of the exiting (supposed saturated) steam flowing in the heating coil—, the primary pressure, , and the secondary pressure, The relations between the different pressures around the ejector areThe mass balance for the ejector writeswhere stands for the entrainment ratioThe enthalpy of exiting flow can be deduced from the energy balance (iii)Heating Coil
Assuming a difference of 5 K between the temperatures of the heat source and that of the refrigerant generator solution, we getThe mass balance writes(iv)Water Pump
We suppose approximately isothermal pumpingThe mass and energy balances write, successively,where the term in the last equation represents the specific pump work (kJ/kg), with (v)Expansion Valve
The expansion is isenthalpic, i.e.,
3.2. Liquid Solution Loop
The absorbergenerator loop comprises absorber, solution valve, solution pump, solution heat exchanger, and refrigerant generator.(i)Refrigerant Generator
With denoting the lithium bromide concentration in the liquid solution, the mass balances for this machine element writeSolving for yields For the energy balance we getfrom which we deduceThe properties of waterweak solution exiting the generator are determined as follows:For known solution temperature and pressure, the saturation concentration can be deduced from solution property relations. Following equations fix the properties of exiting vapor at (ii)Solution Heat Exchanger
Besides the trivial relationsMass and energy balance equations writeConsidering the heat exchanger effectiveness, , we have the following further relations:(iii)Solution Valve
Through the solution valve, the pressure is reduced from condenser to evaporator pressure. In addition to the usual mass balanceequations and we have the relations(iv)Solution Pump
Again, we have the trivial mass balances and As for the waterpump, the pumping process is assumed isothermal . During pumping, the enthalpy of the refrigerantrich solution from absorber is increased by , with ,(v)Absorber
Per definition, and . For the liquid solution exiting the absorber we get in addition to the mass and energy balance equationsThe property relations are
3.3. Refrigerant Loop
(i)Condenser
Streams and flow in the condenser where they condensate. Condensing temperature and pressure are and , respectively. The mass and energy balances around the condenser writeKnowing the condensation temperature , pressure as well as the enthalpy of exiting liquid can be deduced as(ii)Refrigerant Expansion Valve
Liquid refrigerant undergoes a pressure reduction before it enters the evaporator. Evaporation temperature and pressure are and , respectively.
For fixed evaporator temperature and assuming saturated vapor at exit, we can write .
The mass and energy balances for the valve write(iii)Evaporator
The evaporator equations areThe of the proposed absorption system, when neglecting all pump work, can be expressed as
4. Ejector 1D Model and Analysis
Because the performances of the proposed cycle depend largely on ejector performances, a reliable ejector model is necessary for the cycle simulations. In this paper, the ejector is modelled basing on the 1D analyses in [25, 26].
In this type of model, it is assumed that(i)primary fluid expands isentropically in nozzle, and the exiting flow compresses isentropically in diffuser(ii)inlet velocities of primary and entrained fluids are insignificant(iii)velocity of the compressed mixture at ejector outlet is neglected(iv)mixing of primary and secondary fluids in the suction chamber occurs at constant pressure(v)flow in ejector is adiabatic
Isentropic efficiencies are introduced in the model to account for eventual irreversibility in the expansion process in primary nozzle, , in the mixing process of primary and secondary flow in the mixing chamber, , and finally in the compression process in the diffuser, . For the numerical simulations we set , , and .
4.1. Primary Nozzle
In the nozzle, the primary vapor expands and accelerates. The Mach number of the fluid at nozzle outlet plane , deduced from energy balance, writes
In this equation, is the isentropic nozzle efficiency, defined as the ratio between actual enthalpy change and enthalpy change undergone during an isentropic process.
The expression for the area ratio at nozzle throat and outlet is
4.2. Suction Chamber
Because , the secondary fluid expands in the suction chamber and is entrained by the highspeed primary flow. The Mach number of the entrained fluid at nozzle exit plane writes
4.3. Mixing Chamber
Here, primary and secondary fluids are mixed. The properties of the resulting stream at section are deduced from continuity, momentum, and energy equations and expressed as function of the critical Mach number ,As can be noticed, the mixture is written as a combination of critical Mach numbers of the original streams, and . in this equation stands for the temperature ratio of incoming streams and :The relationship between and at any point of the ejector is given by the equationBy the end of the mixing chamber, a shock wave occurs at section (). The flow changes from supersonic to subsonic conditions, producing simultaneously a sudden rise in the static pressure. The relation between the Mach number upstream and downstream of the shock wave is given byThe corresponding pressure increase writes
4.4. Diffuser
The expression of the pressure lift in the diffuser is
The ejector area ratio , i.e., the ratio of nozzle throat area and diffuser constant area section, writes
5. Results and Discussion
The EES machine model program is run to thermodynamically analyze the proposed hybrid singleeffect absorption refrigeration system. The thermophysical properties of LiBrH2O solution are estimated using the software property data and modelbank.
The simulations are performed for the conditions given in Table 1. Evaporator temperature is set to 4°C, condenser temperature to 37°C, and absorber temperature to Condenser and absorber are both supposed watercooled. The cooling medium is processed thereafter in a cooling tower.

5.1. Program and Machine Model Validation
The simulation program is first validated by comparing our simulation results for a conventional singleeffect cycle with the results published by Somers (2009) [27] for the same operating conditions: evaporator temperature,1.3°C; condenser and absorber temperatures at 40.2°C and 32.7°C, respectively; effectiveness of solution heat exchanger, 0.5; mass flow rate of solution leaving absorber, 1 kg/s. As can be noticed when comparing the results in columns 2 and 3 of Table 2, both sets of data are in very good agreement. Therefore, we can now proceed to the simulations of the proposed hybrid cycle with some confidence.
The next step was to validate the adequacy of the conventional model by comparing the predicted, calculated performance with experimental data reported in [28] concerning a large capacity LiBrchiller. Two different sets of operating conditions are considered. As can be observed when studying columns 4 to 7 in Table 2, the calculated data is for both tests very close to the reported data in [28]. Finally, the proposed ejector configuration model is validated using the only available experimental data found in the literature [29]. As represented in Figure 3, a fair agreement between calculated and reported data is noticed. Discrepancy may have its source in inaccuracy of experimental and/or too simple ejector model (ideal gas behavior).
5.2. Comparison of Hybrid and Conventional Cycle Performances
For purpose of illustration, the chiller cycle is represented in Figure 4 in the usual Oldhamdiagram and in the water diagram in Figure 5.
We now proceed to the comparison of the performances of the proposed cycle and the conventional basic cycle (without ejector) for varying machine generator called also desorbertemperature (Figure 6), condenser temperature (Figure 7), and evaporator temperature (Figure 8).
As depicted in Figures 6–8, the coefficient of performance of the hybrid cycle is in all cases larger than the of the conventional cycle for the same operating conditions.
However, this performance enhancement is restricted to a specific interval of machinegenerator temperature, as Figure 6 clearly shows. Outside this temperature interval, both cycles are practically equivalent. Figure 6 shows also that with growing desorber temperature the curve of the hybrid cycle first exceeds that of the basic cycle, reaches a maximum than decreases gradually, and resumes the curve of the conventional cycle . It is also worth noticing that the of the hybrid cycle under optimal conditions approaches the of doubleeffect conventional cycle.
Figures 7 and 8 depict the evolution of the of both cycles with condenser and evaporator temperature, respectively, for . Note that is the steam generator temperature, not the chiller desorber temperature, the abscissa in Figures 6–14. Both are expectably decreasing in the first case and increasing in the second. is always larger than of conventional cycle because the constant maintained desorbertemperature is set to 80°C, i.e., in the favourable interval 70°C–90°C. In conclusion of this section we notice that an ejector incorporated in the hybrid cycle (i) improves the cycle performances and (ii) the maximal is reached at lower machine generator temperature.
5.3. Performances of the Hybrid Cycle
The effect observed previously in Figure 6 (enhancement of the cycle performance due to the incorporation of ejector in the driving compartment of the machine) depends on the primary flow pressure used to activate the ejector. Increasing this pressure expands this effect in magnitude and amplitude as Figure 9 shows: the higher the steamgenerator pressure (and consequently temperature), the larger the machinegenerator temperature range where the cycle performance is improved, and the higher the maximum that could be reached inside this interval. On the opposite, when the steam generator pressure is decreased to 10 bar, practically no improvement more of the cycle performance is observed under the prevailing conditions.
Figure 10 depicts the evolution of with by varying the condenser temperature, . It is observed that the typical pink curve of Figure 6 is expectedly shifted to lower machinegenerator temperatures (with lower condenser temperature, less high desorber temperature is needed to activate the cycle) with however concomitantly increased maximal and enlarged favorable temperature interval, where the cycle performance is improved.
Similar effects are observed in Figure 11 depicting the evolution of with by varying evaporator temperature. Here, the typical COP—improved portion of the curve is shifted to lower —values when the evaporator temperature is increased, a thermodynamically more favourable situation. The of the hybrid cycle rises from 0.85 to 1.12 for generator temperature decreasing from 78°C to 67°C when the evaporator temperature increases from 4°C to 12°C.
5.4. Ejector Performance
The ejector model presented in Section 4 will help us interpret the represented simulation results in Figures 7–11 and assess the beneficial effect—and limits—of integration of an external ejector loop to a conventional absorption cycle. We first investigate the relation between the performance of the incorporated ejector, i.e., its entrainment ratio , and significant absorption machine parameters, namely, desorber temperature , evaporator temperature , and condenser temperature . Figure 12 depicts the evolution of with . For a given primary pressure , the entrainment ratio decreases monotonously with and finally vanishes for a maximal value of the desorber temperature; i.e., secondary flow is no more entrained inside the ejector. The ejector is then offdesign and its geometry should be changed. Same behaviour of vs. is noticed if the steam pressure is increased. However, in this case the curve is shifted upwards to larger values of ; i.e., more secondary vapour is sucked in the ejector for a given temperature , and the limit value of where the entrainment ration vanishes is pushed farther away.
Similar behaviour is observed in Figure 13, when for fixed primary pressure the condenser temperature (secondary pressure) is varied. If the condensation temperature is reduced (or alternatively enlarged), the entrainment ratio is also decreased (or increased, respectively). However, the curves vs. for the various condenser temperatures all converge to the same point on the temperatureaxis where vanishes. This temperature depends solely on the primary steam pressure.
Finally, Figure 14 shows that the evaporator temperature has practically no effect on the ejector performance by fixed and , as all vs. for the various tested are superimposed.
According to the ejector model presented in Section 3 of the present paper, the entrainment ratio depends on six independent parameters: nozzle area ratio, primary flow and secondary flow properties, and backpressure, i.e., . The results presented in the foregoing sections are obtained for simulations with the specific conditions: (i) constant ejector nozzle ratio set to ; (ii) saturated ejectordriving steam; i.e., and are then no more both independent; (iii) pressure of secondary flow equals condenser pressure, an independent parameter; (iv) temperature of flow is not an independent variable. It depends on the processes taking place in rest of the absorption chiller and in particular on the backpressure, , which is considered here as an independent parameter.
In summary, the entrainment ratio depends then on just three parameters
Figure 15 illustrates this dependency for a fixed secondary pressure, bar, as it is the case for the data depicted in Figures 6, 7, and 12. For a constant drivingsteam pressure , increases with falling backpressure, becomes a maximum, and decreases thereafter abruptly to zero. More generally, on increasing the ejector backpressure by fixed ejector geometry, a gradual reduction in entrainment ratio is induced. The maximal value of is the larger; i.e., the greater the improvement, the higher the . Further, when becomes larger, the interval of backpressure (and hence, the range of as well as the range of desorber temperature, ) where a chiller performance enhancement is expected, expands. The pressure difference drives the ejector, and the difference , where is the pressure at nozzle exit, drives the entrainment process (Eq. ). With increasing primary pressure, rises and comes closer to the secondary flow pressure . The suction of the secondary flow into the mixing chamber declines gradually and eventually vanishes for . Consequently, at this limit reached for , falls to zero. The vertical isobarplane sets a geometrical limit to the used nozzle design.
The plane limits also the 3D surface of Figure 15. The calculations show that the Mach number of the mixed stream is there equal to , the Mach number of the primary flow at nozzle exit; i.e., the mixed gas mass flow rate reduces to that of the primary flow and practically no secondary gas is entrained. This constitutes a higher limit for the design of the ejector area ratio , which comes then very close to the nozzle area ratio, . The maximum value of is found for minimal values of backpressure. At the limit, the Mach number of mixed gas is the lowest and equals that of the entrained secondary flow .
The curves represented in Figures 6–9 depict its evolution when the effects of both the ejector and the singleeffect absorption chiller are combined. By increasing the backpressure and, consequently, the desorber temperature, the tends first to increase as it does for a conventional cycle. The entrainment ratio however is decreasing. The resulting outcome is then first an increase of and then a decrease after passing a maximum where opposed effects cancel each other.
6. Conclusion
A hybrid singleeffect cycle with water lithiumbromide as working fluid and activated by a steamejector loop is proposed and theoretically investigated. Mathematical models of the hybrid cycle and the ejector are detailed. Results show that entrainment ratio of the ejector depends on activatingsteam pressure, on condenser temperature, and only slightly on evaporator temperature. For a fixed steam pressure, the of the hybrid cycle first surpasses that of the corresponding conventional cycle when the desorber temperature is increased, passes by a maximum, and then resumes the performance of the basic cycle. The maximum of an ejectoractivated cycle is obtained at lower temperatures than that of a conventional system and can reach that of a doubleeffect basic scheme. The span of machine generator temperature where the is enhanced depends on the primary ejector pressure: it is larger for higher pressure. The entrainment ratio of the ejector is found to increase with the steam pressure and to decrease with rising backpressure. However, the performance of the ejector is confined to a specific region of the parametersurface. Outside this domain, the entrainment ratio vanishes and the ejector is offdesign.
Nomenclature
:  Area 
:  Nozzle area ratio 
:  Ejector area ratio 
:  Coefficient of performance 
:  Specific enthalpy (kJ/kg) 
:  Mass flow rate (kg/s) 
:  Mach number 
:  Critical Mach number 
:  Pressure (bar) 
:  Heat transfer rate (kW) 
:  Universal gas constant (kJ/(kg K)) 
:  Temperature (°C) 
:  Work transfer rate (kW) 
:  Steam quality 
:  Ratio of steam specific heats 
:  Heat exchanger effectiveness 
:  Nozzle, mixing, and diffuser efficiency 
:  LiBr concentration in solution (mass. %) 
:  Density (kg/m^{3}) 
:  
:  Entrainment ratio . 
:  Absorber 
:  Backpressure 
:  Constant section area (ejector) 
:  Condenser 
:  Diffuser (ejector) 
:  Evaporator 
:  Generator 
:  Nozzle exit plane (ejector) 
:  Plane in mixing chamber (ejector) 
:  Shockwave plane 
:  Mixing chamber (ejector) 
:  Nozzle (ejector) 
:  Saturation 
:  Solution 
:  Steam generator 
:  Water 
1–19:  Referred state points. 
Data Availability
The data used to support the findings of this study are available from the corresponding author upon request.
Conflicts of Interest
The authors declare that they have no conflicts of interest.
References
 G. Besagni, R. Mereu, and F. Inzoli, “Ejector refrigeration: A comprehensive review,” Renewable & Sustainable Energy Reviews, vol. 53, pp. 373–407, 2016. View at: Publisher Site  Google Scholar
 G. Besagni, “Ejectors on the cutting edge: The past, the present and the perspective,” Energy, vol. 170, pp. 998–1003, 2019. View at: Publisher Site  Google Scholar
 G. Besagni, R. Mereu, P. Chiesa, and F. Inzoli, “An Integrated Lumped ParameterCFD approach for offdesign ejector performance evaluation,” Energy Conversion and Management, vol. 105, pp. 697–715, 2015. View at: Publisher Site  Google Scholar
 L. Shi, J. Yin, X. Wang, and M. Zhu, “Study on a new ejection–absorption heat transformer,” Applied Energy, vol. 68, no. 2, pp. 161–171, 2001. View at: Publisher Site  Google Scholar
 A. Sözen and M. Özalp, “Performance improvement of absorption refrigeration system using triplepressurelevel,” Applied Thermal Engineering, vol. 23, no. 13, pp. 1577–1593, 2003. View at: Publisher Site  Google Scholar
 C. Vereda, R. Ventas, A. Lecuona, and M. Venegas, “Study of an ejectorabsorption refrigeration cycle with an adaptable ejector nozzle for different working conditions,” Applied Energy, vol. 97, pp. 305–312, 2012. View at: Publisher Site  Google Scholar
 L. Garousi Farshi, A. Mosaffa, C. Infante Ferreira, and M. Rosen, “Thermodynamic analysis and comparison of combined ejector–absorption and single effect absorption refrigeration systems,” Applied Energy, vol. 133, pp. 335–346, 2014. View at: Publisher Site  Google Scholar
 A. Khaliq, R. Kumar, and E. M. Mokheimer, “Investigation on a solar thermal power and ejectorabsorption refrigeration system based on first and second law analyses,” Energy, vol. 164, pp. 1030–1043, 2018. View at: Publisher Site  Google Scholar
 S. Yosaf and H. Ozcan, “Exergoeconomic investigation of flue gas driven ejector absorption power system integrated with PEM electrolyser for hydrogen generation,” Energy, vol. 163, pp. 88–99, 2018. View at: Publisher Site  Google Scholar
 D.W. Sun, I. W. Eames, and S. Aphornratana, “Evaluation of a novel combined ejector  Absorption refrigeration cycle  I: Computer simulation,” International Journal of Refrigeration, vol. 19, no. 3, pp. 172–180, 1996. View at: Publisher Site  Google Scholar
 H. S. Majdi, “Performance evaluation of combined ejector LiBr/H2O absorption cooling cycle,” Case Studies in Thermal Engineering, vol. 7, pp. 25–35, 2016. View at: Publisher Site  Google Scholar
 A. M. Abed, K. Sopian, M. Alghoul, H. S. Majadi, and A. N. AlShamani, “Experimental evaluation of single stage ejectorabsorption cooling cycle under different design configurations,” Solar Energy, vol. 155, pp. 130–141, 2017. View at: Publisher Site  Google Scholar
 E. Bellos and C. Tzivanidis, “Parametric analysis and optimization of a cooling system with ejector absorption chiller powered by solar parabolic trough collectors,” Energy Conversion and Management, vol. 168, pp. 329–342, 2018. View at: Publisher Site  Google Scholar
 S. Toghyani, E. Afshari, and E. Baniasadi, “Performance evaluation of an integrated proton exchange membrane fuel cell system with ejector absorption refrigeration cycle,” Energy Conversion and Management, vol. 185, pp. 666–677, 2019. View at: Publisher Site  Google Scholar
 S. Aphornratana and I. W. Eames, “Experimental investigation of a combined ejectorabsorption refrigerator,” International Journal of Energy Research, vol. 22, pp. 195–207, 1998. View at: Google Scholar
 R. Sirwan, M. Alghoul, K. Sopian, Y. Ali, and J. Abdulateef, “Evaluation of adding flash tank to solar combined ejector–absorption refrigeration system,” Solar Energy, vol. 91, pp. 283–296, 2013. View at: Publisher Site  Google Scholar
 A. M. Abed, M. Alghoul, R. Sirawn, A. N. AlShamani, and K. Sopian, “Performance enhancement of ejector–absorption cooling cycle by rearrangement of solution streamlines and adding RHE,” Applied Thermal Engineering, vol. 77, pp. 65–75, 2015. View at: Publisher Site  Google Scholar
 D. Hong, G. Chen, L. Tang, and Y. He, “A novel ejectorabsorption combined refrigeration cycle,” International Journal of Refrigeration, vol. 34, no. 7, pp. 1596–1603, 2011. View at: Publisher Site  Google Scholar
 L. G. Farshi, S. S. Mahmoudi, M. A. Rosen, and M. Yari, “Use of lowgrade heat sources in combined ejector–double effect absorption refrigeration systems,” Journal of Power and Energy, vol. 226, no. 5, pp. 607–622, 2012. View at: Publisher Site  Google Scholar
 Y. Shi, F. Li, D. Hong, Q. Wang, and G. Chen, “Experimental study of a new ejectorabsorption refrigeration cycle driven by multiheat sources,” Applied Thermal Engineering, vol. 133, pp. 604–612, 2018. View at: Publisher Site  Google Scholar
 I. W. Eames and S. Wu, “A theoretical study of an innovative ejector powered absorption–recompression cycle refrigerator,” International Journal of Refrigeration, vol. 23, no. 6, pp. 475–484, 2000. View at: Publisher Site  Google Scholar
 D. Sioud, M. Bourouis, and A. Bellagi, “Investigation of an ejector powered doubleeffect absorption/recompression refrigeration cycle,” International Journal of Refrigeration, vol. 99, pp. 453–468, 2019. View at: Publisher Site  Google Scholar
 D. Sioud, R. Garma, and A. Bellagi, “Thermodynamic analysis of a solar combined ejector absorption cooling system,” Journal of Engineering, vol. 2018, pp. 1–12, 2018. View at: Publisher Site  Google Scholar
 F. Klein and S. A. Alvarado, “Engineering equation solver,” Middleton, WI: F–chart software. View at: Google Scholar
 H. ElDessouky, H. Ettouney, I. Alatiqi, and G. AlNuwaibit, “Evaluation of steam jet ejectors,” Chemical Engineering and Processing: Process Intensification, vol. 41, no. 6, pp. 551–561, 2002. View at: Google Scholar
 B. Huang, J. Chang, C. Wang, and V. Petrenko, “A 1D analysis of ejector performance,” International Journal of Refrigeration, vol. 22, no. 5, pp. 354–364, 1999. View at: Publisher Site  Google Scholar
 C. Somers, Modelling absorption chillers in Aspen.Simulation of absorption cycles for integration into refining processes [Masters of Science], University of Maryland, College Park, MD, USA, 2009, https://scholar.google.com/scholar_lookup?title=Modelling%20Absorption%20Chillers%20in%20aspen%2C%20%E2%80%9CSimulation%20of%20Absorption%20Cycles%20For%20Integration%20Into%20Refining%20processes%E2%80%9D&author=C.%20Somers&publication_year=2009.
 M. L. Chougui, Simulation et étude comparée de cycle à absorption (LiBr/H2O) à usage de froid. Cas de l’unité de production de Henkel [Master], Université Mentouri, ConstantineAlgérie, 2010, https://scholar.google.com/scholar?hl=en&as_sdt=0%2C5&q=Simulation+et+%C3%A9tude+compar%C3%A9e+de+cycle+%C3%A0+absorption+%28LiBr%2FH2O%29+%C3%A0+usage+de+froid.+Cas+de+l%E2%80%99unit%C3%A9+de+production+de+Henkel&btnG=.
 I. W. Eames and S. Wu, “Experimental proofofconcept testing of an innovative heatpowered vapour recompression–absorption refrigerator cycle,” Applied Thermal Engineering, vol. 20, no. 8, pp. 721–736, 2000. View at: Publisher Site  Google Scholar
Copyright
Copyright © 2019 Doniazed Sioud and Ahmed Bellagi. This is an open access article distributed under the Creative Commons Attribution License, which permits unrestricted use, distribution, and reproduction in any medium, provided the original work is properly cited.